OEM Factory Bare ACSR/Aw Linnet Aluminium Clad Steel Reinforced
|FOB Price:||US $0.2 / Meter|
|Min. Order:||1,000 Meters|
|Min. Order||FOB Price|
|1,000 Meters||US $0.2/ Meter|
|Production Capacity:||2000 Ton per Month|
|Transport Package:||Wooden Drum, Steel Drum, Steel&Wooden Drum|
|Payment Terms:||L/C, T/T, D/P|
- Model NO.: ACSR
- Voltage: Low and Medium Voltage Cable
- Insulation Material: Bare
- Material Shape: Round Wire
- Certification: ISO, CCC, CE
- Trademark: Jinshui cable
- Origin: ZHENGZHOU CABLE
- Application: Overhead
- Current: AC Cable
- Sheath Material: Bare
- Wire Core Material: Aluminum
- Brand: Jinshui
- Specification: ASTM, BS, IEC
Aluminum Conductor steel reinforced ACSR
Conductor(AAC and ACSR) have been widely used in power transmission lines with various voltage levels,because they have such good characteristics as simple structure,convenient installation and maintenance,low cost large transmission capacity.And they are also suitable for laying across rivers valleys and the places where special geographical features exist.
(1).The permissible long-time operating temperature for aerial conductor is 70oC.
(2).Under the circumstance that rare climate is occuring and ice coverage rate low in heavy ice area,the biggest stress of cable at the lowest point of the sag should not exceed 60% of the short-time destructive power.
(3).When connecting conductors,the conductor beside the connecting tube cant be prominent.Otherwise,the force on the operating conductors will be unbalanced.After connectors are install,the connecting tube should be painted by moisture-proof varnish in order to protect it from corrosion.
(4).Under installaion,the arc downing stress of all the conductors should be the same.With in the permissible distance of crossing buildings or dropping to the ground,the stress can be 10-15% higher than regular stress.
(1).The electrical performance of AAC and ACSR is indicated in DCΩ/km(20oC).The resistivity of the hard aluminum wire for stranded wires is not greater than 28.264 nΩ. m of international standard value.
(2).The rated tensile strength of AAC is denoted with the result of total cross-section of all aluminum conductors multiplied by min.tensile of corresponding size specified in the standard for aluminum wire.
(3).The rated tensile strengh of ACSR is denoted with sum of all aluminum conductorstensile strength and steels tensile strength.
a.The tensile strength of all aluminum conductors is denoted with the result of all cross-sections of aluminum conductors multiplied by min.tensile strength of corresponding size specified in the standard for aluminum wire.
b.The tensile strength of all steel wire is denoted with the result of all cross-sections of steel wires multiplied by the stress at 1% elongation of corresponding size specified in the standard for steel wire.
(1).The hard aluminum conductor used for AAC and ACSR conforms to the standard GB/T 17048-1997(equivalent to IEC 60889:1987).
(2).The zinc coated steel wire used for ACSR conforms to IEC 60888:1987.
(3).Production can be arranged according to customers requirements for material standard,etc.
Construction of All Aluminum Conductor and Aluminum Conductor Steel Reinforced.